Prices incl. VAT plus shipping costs
Ready to ship today,
Delivery time appr. 1-3 workdays
- Order number: 301001
QuickTherm underfloor heating consists of easy-to-lay system panels. The system panels combine the pipe duct and insulation (EPS DEO WLG 035) at a height of just 30 mm. The pipe ducts are designed for the QuickTherm MVR heating pipe. Thanks to the pipe ducts, the heating pipe must not be inconveniently fixed - the laying clearance of 16.7 cm is automatically maintained. The system panels are provided with predetermined breaking points and can therefore be customised to the room without the use of tools. The attached heat conducting plates made of aluminium ensure a quick, complete and even transfer of heat to the floor covering.
Instead of a wet screed, the QuickTherm system panel can be directly laid with dry screed, specialist load distribution panels or with laminate and ready-made parquet.
• Dimensions: 1000 x 500 x 30 mm
• To take 3 pipes per system panel
• Laying clearance of heating pipes: 16.7 cm
• 6 m of heating pipe per m²
• Suitable for the QuickTherm heating pipe MVR ø 16 mm
• Insulation material: EPS DEO WLG 035
• Also suitable for wet screed
Why do you offer only two heating systems?
QuickTherm and GreenLine underfloor heating are universal systems. They can be installed as floor, wall or ceiling heating and are suitable for various types of flooring. This is of benefit to you as the systems remain compatible, wherever they are used.
Which type of floor covering can I use with QuickTherm?
This depends on the desired floor installation. Depending on the installation (direct laying, dry or wet screed) various top coverings are possible. You can find an overview of possible variations here.
Which components do I need for floor heating?
This depends on the desired floor installation. Basically you need to calculate the system components according to the following key.
Per square metre of underfloor heating you need:
6,00 metres of MVR heating pipe
1,45 x system panels
0,25 x deflection bends
0,30 x filling panels
0,96 x heat distribution plates
1,00 metre of edge insulation strips
On top of that you need control components. You can find out how to select them here.
Alternatively you can also choose one of the QuickTherm complete kits. These sets are compiled to suit various floor constructions and flooring surfaces.
What distance do the heating pipes have when fitted?
The QuickTherm system consists of system panels. This means that the fitting distance of 166 mm is pre-defined for the integrated pipe ducts and is therefore automatically maintained.
How long can a heating circuit be as a maximum?
The pipe for a heating circuit is a maximum of 100 m. As 6 metres of heating pipe are fitted per square metre, one heating circuit can cover up to 15 square metres. Two or more heating circuits are laid in larger rooms.
What is the maximum length of a heating circuit?
The length of a heating circuit should be no longer than 100 m. As 6 metres heating pipes be laid per square metre underfloor heating, a heating circuit can cover up to 15 square metres. This means that two or more heating circuits are installed in larger rooms.
Do I need specialised tools for fitting my floor heating?
Yes, we urgently advise this. You can buy all the tools you need for fitting our systems in the shop.